It is very important to check the dry powder fire extinguishing equipment regularly in the fire fighting equipment inspection
月检内容?1.检项目及周期 下列项目至少每月检查1ci。?干粉储存zhuangzhi部件。?驱动气体储瓶chongzhuang量。?2.检内容 检查干粉储存zhuangzhi部件shifu有碰zhuang或机械xingsunshang，fang护涂层shifu完好;铭pai、biaozhi、铅封应完好。 对二yanghua碳驱动气体储瓶逐个进行chen重检。
The following items shall be checked at least once a month. Components of dry powder storage device. Drive gas bottle filling capacity. 2. Inspection contents: check whether there is collision or mechanical damage to parts of dry powder storage device and whether the protective coating is intact; Nameplates, marks and seals shall be intact. Weighing and checking the carbon dioxide driven gas storage bottles one by one.
季检的内容he要求 tongguo试验fa对泵组式xitong进行1ci放shui试验，检查泵组启动、主备泵切换及报警联动功能shifu正常。 检瓶组式xitong的kongzhifa动zuoshifu正常。 检查管道he支、吊架shifu松动，管道连jie件shifubian形、laohua或有裂纹等xian象。
Contents and requirements of the quarterly inspection: conduct a water discharge test on the pump group system through the test valve to check whether the pump group starts, the switch between the main and standby pumps and the alarm linkage function are normal. Check whether the control valve of the bottle assembly system operates normally. Check whether the pipe and support, hanger is loose, whether the pipe connection deformation, aging or crack phenomenon.
(2)年检的内容he要求 ding期测ding1cixitongshui源的gongshui能力。 对xitong组件、管道及管件进行1ciquan面检查，清洗储shuixiang、guo滤器，bing对kongzhifa后的管道进行吹扫。 储shuixiang每半年换shui一ci，储shui容器内的shui按chan品zhizaoshang的要求ding期更换。 进行xitong模拟联动功能试验，试验内容与要求详见第四节第三部分。biao准要求二yanghua碳博猫登录网址器每年至少检查一ci，低于额dingchongzhuang量的95%就应进行检修。 由于石油hua工设备及受压容器，在wen度应力、交bian应力、介zhi强lie腐蚀等恶劣条件的zuo用下，容易出蟴hong孤瑉ao成火灾hezhongdu事故。
(2) contents and requirements of annual inspection: regularly determine the water supply capacity of system water source once. Conduct a comprehensive inspection of the system components, pipes and fittings, clean the water storage tank and filter, and purge the pipes behind the control valve. The water in the storage tank shall be changed every six months, and the water in the storage tank shall be changed periodically according to the requirements of the manufacturer. Carry out the system simulation linkage function test. See the third part of the fourth section for the test content and requirements. Carbon dioxide fire extinguishers are required to be checked at least once a year. Maintenance should be carried out when they are less than 95% of the rated filling capacity. Due to the petrochemical equipment and pressure vessels, in the temperature stress, alternating stress, medium strong corrosion and other adverse conditions, easy to leak, resulting in fire and poisoning accidents
Therefore, every year to do a sampling inspection, when necessary, but also to do 100 percent of the inspection. On the premise of not affecting the external structure of ancient buildings, tall ancient buildings should be installed lightning protection facilities according to the needs of terrain and objects, and the test and maintenance should be carried out before the annual thunderstorm season to ensure good condition and effectiveness.
(3)模拟启动检。 2.检内容 fang护qu的疏散tong道、疏散指示biaozhihe应急照明zhuangzhi、fang护qu内he入口处的声光报警zhuangzhi、入口处的安quanbiaozhi糰n煞鄄┟ǖ锹纪芳僚绶胖甘久诺啤⑽辌huang或固dingchuangshan的di上fang护quhedi下fang护qu的舙ai鴝huangzhihe门chuang设有密封条的fang护qu的泄压zhuangzhi。储存zhuangzhuangzhi间的位zhi、tong道、耐火等级、应急照明zhuangzhi及di下储存zhuangzhi间机械排fengzhuangzhi。 管网，支架及喷放组件 干粉储存容器的数量、型号he规格，位zhi与固dingfang式，油漆hebiaozhi，干粉chongzhuang量，以糰n煞鄞⒋嫒萜鞯陌瞶huangzhi量。 集流管、驱动气体管道he减压fa的规格、连jiefang式、布zhi及其安quanfang护zhuangzhi的泄压fang向。
(3) simulate startup check. 2. Review the content protection the evacuation passageway and evacuation instructions signs and emergency lighting devices, protective zone and the acousto-optic alarm device, the safety sign at the entrance at the entrance and dry powder discharge indicator lamp door, no window sash or fixed protection zone of the ground and underground protective of the doors and Windows with sealing strip and exhaust pressure relief device of protection zone. Location, passageway, fire resistance rating, emergency lighting and mechanical ventilation between storage and installation. Quantity, type and specification of dry powder storage containers for pipe networks, supports and spraying components, position and fixing method, paint and marking, dry powder filling amount, and installation quality of dry powder storage containers. Specification, connection, arrangement and direction of pressure relief of collector pipe, driving gas pipe and pressure reducing valve.
?选zefa及信号反馈zhuangzhi的数量、型号、规格、位罝、biaozhi及其安zhuangzhi量。 fa驱动zhuangzhi的数量、型号、规格hebiaozhi，安zhuang位罝，气动fa驱动zhuangzhizhong启动气体储瓶的介zhi名chen簍ong鋤huang压力，以及启动气体管道的规格、布zhihe连jiefang式。 管道的布罝与连jiefang式、支架he支吊架的位罝及间距、穿guo建筑gou件及其bian形缝的处li、各管段he附件的型号规格以及fang腐处lihe油漆颜色; 喷蚮an氖俊⑿秃拧⒐娓瘛瞶huang位zhihefang向。 博猫登录网址kongzhi器及手动、自动转换kai关，手动启动、停止按niu，喷放指示灯、声光报警zhuangzhi等联动设备的设zhi。
Select valve and signal feedback device quantity, model, specification, location, logo and installation quality. The e number, model, specification and logo of valve drive device, installation location, medium name and filling pressure of starting gas storage bottle in pneumatic valve drive device, as well as the specification, layout and connection mode of starting gas pipeline. Piping layout and connection, support and hanger position and spacing, through the building components and deformation joints of the treatment, the pipe section and accessories of the model specifications as well as anti-corrosion treatment and paint color; The number, model, specification, installation position and direction of sprinkler head. Setting of fire extinguishing controller, manual and automatic switch, manual start and stop buttons, sprinkling indicator light, sound-light alarm device and other linkage equipment.